The Plumbing Code
The Code outlines the best and most modern methods
to be used in plumbing installations. Since the plumbing in any private
or public building is a part of the community water and sewage disposal
system, it is vital that such installations should not be left to the
discretion of irresponsible individuals. The protection of the public
health and safety must be maintained by the establishment of sound code
A plumbing or sanitation code is not a plumber's code.
It is rather a set of Rules and Regulations imposed by cities, counties
and states on anyone who undertakes any work involving the installation
of drinking water, sewer or toilet facilities in homes, offices, factories,
schools and hospitals. Regardless of who might do the work, plumbing and
sanitation codes require that it be done in a specific, safe manner because
it was found that failure to do so caused widespread disease, which can
be crippling and deadly-to the community.
Plumbers must demonstrate their competence as installers
of plumbing systems to an official executing board prior to being issued
a license. A plumbing code which is technically perfect is valueless if
in provisions are not observed and enforced. The issuance of a license
by a community specifies that in holder is qualified both theoretically
and practically and that their technical knowledge is sufficient to maintain
the standards of the code.
Is licensing intended to prevent anyone but a plumber
from doing sanitation work? NO... Licensing prohibits the irresponsible,
incapable person from endangering the health of your family, neighbors
sad community. Any person may do the work who has sufficient knowledge
to do it in a safe manner, so long as the Rules and Regulations of the
plumbing and sanitation code are observed. However, those wishing to do
such work must demonstrate their ability by taking out a license and passing
The State requires that, like a doctor, nurse, dentist
or pharmacist, anyone whose work affects the public health and safety
shall have adequate knowledge and training. No one wants a "quack doctor"
to treat his family or a "soda clerk" to fill his prescriptions. For precisely
the same reasons, one does not want a "handyman" to do work in his home,
office factory which can adversely affect the health of his family, his
employees or his neighbors.
Done improperly this work would probably need to be
rectified at the time the property changed hands which means paying twice
for the same work.
Inspection and Permits
Through the issuance of permits and the requirements
of public inspection, a community can assure itself of proper plumbing
code enforcement. The permit allows the plumbing inspector to protect
the consumer by assuring plumbing installations are done properly. The
inspection of such plumbing work insures that the installation is being
completed in accordance with code provisions.
It Pays to Take Care of Our Plumbing.
The average household plumbing system represents an
investment of about fifteen percent of the value of the house. No part
of the house is more important . Nothing in the house is used more often.
A smoothly functioning plumbing system is a pin to health and adds to
the convenience of modern living.
This booklet was written with the objective of helping
home owners as well as renters keep their plumbing systems in good operating
condition. The sale value of a house with sound plumbing is far greater
than that of a house where plumbing is in poor repair.
There are many things that an owner or renter can
do; there are many things that should be left to an expert-theplumbing
contractor and his staff of journeymen plumbers. Minor repairs should
be made promptly. Such annoyances such as a clogged
drain, dripping faucet or a leaking flush valve in the toilet, are
more than a mere bother - they usually waste money. This booklet suggests
remedies for these and many other household plumbing problems.
Major repairs, replacements, and new plumbing installations
should be left to the supervision of a plumbing contractor. His working
methods are based on years of experience - and his guarantee is assurance
that all materials and methods are of the highest quality.
This booklet will help prolong the useful life of
your plumbing system. Your plumber will be glad to give you additional
hints that apply specifically to your own home.
Plumbers get more calls to open clogged drains than
for any other service. Many such calls could be prevented by greater care
in the use of drains. The most-used drain is the one in the kitchen sink
and that is the drain most often clogged.
Preventing this situation can be done by carefully
watching what is emptied into the sink drain and by the regular use of
a safe biodegradable waste digester. Your plumber can give you more information
on these products.
Sink stoppages are usually caused by liquid fats,
emulsified by warm dishwater and carried through the pipes. The water
cools as it proceeds to the main sewer and leaves the fatty deposits along
the way. A film of grease forms on the pipe wall, then another and another.
Coffee grounds and bits of food add to this accumulation layer until the
pipe becomes impassible.
Pour excess grease into a tin can and throw it out
with the garbage, not down the sink drain. When using a food disposer,
always let sufficient cold water run to carry the particles down and into
the main line to prevent buildup in the smaller waste lines.
In the event of a stoppage, you should have a "plumber's
friend," or plunger - a large rubber suction cup with a wooden handle.
Cup it tightly over the drain and plunge it vigorously several times.
If it is a double drain sink, make sure you seal the other drain, so water
will not splash out into the other bowl or on you. Drain piping can also
be cleaned by removing the J-bend on the trap below the fixture. First
place adhesive tape around the packing nut or wrap the wrench jaws with
cloth to prevent scratching the metal surface. If plastic piping is in
place, do not grip the nuts too tightly with the wrench, as they can crack
Place a bucket directly under the pipe to catch any
dripping from the open pipe. Pull out the clogging material with a piece
of wire or small hand-turned cable. If you take the trap off, have some
new gaskets ready to slip into the joints.
A clogged trap way in a water closet is a ticklish
problem, so be careful with whatever method you use for cleaning the drain.
Most water closets are made of vitreous china which might crack if exposed
to extremely hot water.
A plunger will normally handle simple toilet clogs.
Another method of cleaning a water closet trap or toilet is the use of
an auger with an adjustable, crank-type handle. Known to plumbers as a
"snake," the spring-steel coil is easily worked past the trap and down
the pipe. A three foot auger is inexpensive and will quickly drill through
most clogs. Use the auger carefully. Careless handling may crack the toilet.
If the rubber-cupped plunger or the auger does not
clear the toilet, call your plumber.
When trying to clear a plugged bathtub drain, place
a heavy cloth in the bottom of the bathtub so your shoe soles won't scratch
the bath's enameled surface. Hold your hand or rag over the waste and
overflow plate, cup the plunger over the drain and plunge it vigorously
several times. If it doesn't open easily, the drain may require cabling
to open it.
Heavy steel spring coils should not be used to clean
traps under lavatories, sinks, or bathtubs. A more flexible type of wire
or spring should be used -- one which is easy to work through the bend
of the trap.
To clean out a floor drain, remove the strainer or
grating which covers the drain box. The dirt and grease can then be dug
out with a spoon or a stick. After a hooked wire or coil spring-steel
auger will clean out the bend or trap. Check to find out whether a removable
clean-out plug has been provided to make this job easier.
When the clogging material has been removed from the
trap, pour a pail or two of hot water into the drain to wash out any loose
material. Check the strainer itself and clean it in hot water and soap
in order to open all holes. The floor drain should be checked regularly,
especially one that is not often used, since water in the trap may evaporate.
This would allow sewer gases to enter the room. Pour a pail of water into
the drain periodically in order to make certain of a proper water seal.
Fittings (faucets and valves) are used more often
than any other part of the plumbing system. They get plenty of use but
are built to take it, under normal conditions.
The best modern fittings are all chrome plated brass
and will last a lifetime under everyday use. They clean easily with soap
and warm water.
Caution: The metal chromium is easily dissolved in
hydrochloric acid and sulfuric acid. Muriatic acid has for years been
considered a good tile cleaner, but only where there are nickel plated
plumbing fittings. Where chrome plating is present, clean bathroom tile
with warm oxalic acid never with muriatic or sulfuric acids. Even covering
the chromium surfaces with cloths will not prevent the acid fumes from
inflicting permanent damage.
Gaining in popularity are polished brass fittings
and trim. These will hold up well, as long as certain precautions are
observed. NEVER use any abrasive cleaner on polished brass. This can scratch
the protective coating on the brass finish resulting in a deterioration
or pitting of the brass plating. Also avoid use of solvent based cleaners
because they can be deleterious to the polished brass finish.
New technologies have brought about the development
of improved finishes that can withstand more wear, but check the manufacturer's
warranty regarding it to determine whether or not you have the "new and
improved" lifetime warranty finish.
Today, most faucets can be categorized as being "washerless
(port-type faucets), or of the Compression (washer) type.
Washerless faucets can be either single handle or
the two handle type. In washerless faucets, the control of the water flow
is done by a replaceable cartridge or arrangement of seals that allow
water flow when the holes or ports are lined up in the proper configuration.
Giving the handle an extra hard twist to stop water flow will be ineffective.
This type of faucet does not use compression strength to stop water flow.
A washerless faucet does not mean it will never leak,
but rather because of the way it is designed, the parts will last much
longer, as their design minimizes friction and wear.
When repairing this type of faucet or requesting service
on one, it is vital that you know the brand name, or have a sample of
the part you require, as there are hundreds of faucet cartridges and parts
kits on the market today.
Your licensedplumber will carry an extensive assortment
of faucet parts in his service truck, but it is impossible to carry absolutely
every part. So it can be very helpful if he knows in advance, the brand
In a compression type faucet, you will find the conventional
setup - a faucet washer on the end of the stern. Replacing the washer
usually will correct a dripping faucet.
However, when removing the stem, always check the
seat inside the faucet body - the brass ring that the washer grinds against.
The faucet seat can be worn or grooved, making the washer replacement
ineffective within days. The washer and seat are the two parts of a compression
type faucet that receives the greatest amount of wear. It is not difficult
to replace a washer. First, shut off the water supply. Usually, the shut-off
valve is under the sink in the kitchen, or in the bathroom, under the
lavatory basin. If there is none, shut off the branch-line valve in the
basement or the main valve where the water supply enters the house.
Pad a smooth jawed wrench with a cloth, then, using
the padded wrench, unscrew the large packing nut and turn out the faucet
stem. Then, with a screw driver that fits the screw slot closely, remove
the screw from the bottom of the stem and pry out the worn washer. If
the screw is tight or stubborn, tap its head lightly or apply penetrating
Next, clean out the washer seat or compartment. When
this is done, insert the new washer of the correct size and composition
for hot or cold water.
Some of the newer, soft neoprene washers are for both
hot and cold water and have a long life. The washer should fit snugly
without having to be forced into position. After inserting, replace the
screw and tighten.
It is usually just as expensive to renew a seat as
it is to buy a new faucet, unless it has been made with a renewable seat.
Check with your plumber about a badly worn faucet.
With cloth over finger, clean the valve seat inside
the faucet. The edge should be smooth and free from deep nicks. If you
find it badly worn, you will probably need to replace the seat or have
the entire faucet replaced by the plumber. Otherwise, it will leak again.
Next, replace the faucet stem and turn it in. Tighten
the packing nut. Be careful not to tighten the nut more than necessary
to stop seepage around the faucet stem.
Remembering that a faucet leaking 60 drops a minute
(not unusual) will waste 2,299 gallons of water every year. Homeowners
should repair leaky faucet at once. You pay twice - once for the water
going through the meter, and then again on your sewer bill, which is based
on water usage.
General Care of Kitchen Sinks
Today, kitchen sink bowls come in many different materials.
Although enameled cast iron remains an attractive and durable product,
many people today are choosing bowls made of stainless steel, and other
solid surface materials for their added durability and stain resistance.
Bowls are available in Corian, Moenstone, Swanstone,
Surrell, and others. The important thing to remember is to follow the
manufacturer's instructions pertaining to the material of which your bowl
is constructed. With some of the solid surface materials, scratches can
be removed when lightly sanded because the color goes throughout the thickness
of the material.
To prolong the life and appearance of enameled cast
iron sinks, clean the bowl immediately after use. Use a non-abrasive
cleaner. Constant use of abrasive cleaners can eventually
wear the finish down, making it much more porous and susceptible to stains.
This can also happen with enameled, cast iron tubs over a long period.
Don't allow fruit or vegetable juices or cleaning
acids to stand on surface. An acid-resisting sink will safely resist lemon,
orange, and other citrus fruit juices, tomato juice, mayonnaise, and other
vinegar preparations if these are not permitted to remain more than a
few hours. A regular enamel finish is not impervious to acids.
Teas and coffee grounds will also stain enameled surfaces,
if allowed to remain very long. Photographic solutions are even more harmful
to enamel, and the amateur photographer should not be allowed to use the
sink, because a fixture once damaged in this way can never be corrected.
When cleaning the sink, use hot water and soap. Water and soap are not
as hard on the enameled finish as strong cleaning solutions like washing
soda or a gritty abrasive. If a cleaner is used, it should be one that
specifically states that it is non- abrasive.
The same precautions mentioned above for kitchen sink
care, pertain to lavatory bowls. Clean them often with hot water and soap.
If a cleaner or cleanser is necessary, use one that is non-abrasive. Today,
it is easy to eliminate the use of glass bottles and jars from the bathroom.
This prevents the possibility of chipping the lavatory bowl if dropped.
If acids or medicine spill on the surface, wash the spills immediately.
Modern bathtubs and showers can be made from a myriad
of materials ranging from the conventional enameled, cast iron and steel,
to fiberglass, acrylic, and man-made materials such as cultured marble.
Many one piece tub or tub and shower combination units are made from gel
coated fiberglass or acrylic plastic.
Never use abrasives on any of these materials. They
can cause scratches to the surface. Usually they will clean with hot water
If that is not sufficient, a cleaning product recommended
by the manufacturer of the fixture, or your plumber, can be used to handle
heavier cleaning tasks.
With fiberglass and acrylic units, special polishes
with no abrasives are available to protect their finishes, by sealing
the pores in the material, which makes subsequent cleaning easier. When
decorating the bathroom or repairing something near the bathtub, place
a heavy cloth over every inch of the bathtub surface so paint, falling
tools, etc., will not mar or chip the enameled surface. Do not stand in
the bathtub with shoes, as the nails and grit in the soles will scratch
the enameled surface. Fiberglass and acrylic hubs should be cleaned with
non- abrasive cleansers recommended by manufacturers.
Closet tanks and bowls are made of vitreous china
and are impervious to ordinary household acids. If something more than
hot water and soap is needed to clean them, apply a non- abrasive powder
or cleaner recommended by your plumber. Many good bowl cleaners are on
the market today. Most plumbers however, have found that the "blue water"
continuous bowl cleaners tend to accelerate the deterioration of the rubber
and neoprene parts in the tank, due to the chemicals they contain.
Seat bumpers should be replaced if worn. Defective
bumpers may cause breakage of the seat or hinges.
Stains or moisture at the base of the closet bowl
indicate that the joint or seal between the closet and its outlet have
failed and should be reset immediately to prevent rotting of the floor,
damage to the plaster of the ceiling below, and possible leakage of sewer
gas into the home.
Water Closet Tanks
If water continues to run into the closet bowl after
the toilet is flushed, it is obvious that some part of the mechanism is
out of order.
When the tank has refilled, if water continues to
seep into the bowl or if there is a low humming noise, this indicates
leakage from the tank. This leakage can occur from either the supply valve
or the improper seating of the rubber tank ball or (flapper) on the discharge
A small amount of food coloring added to the tank
water will help you determine whether the tank ball in the bottom of the
tank is leaking. Add it to the water aver the tank is filled. Watch for
the coloring to seep into the toilet bowl, and if it does, the ball or
flapper over the discharge opening is not water tight If the rubber tank
ball does not fit tightly over the discharge opening, a defective ball,
irregular seat or bent lift wires may be responsible. If the ball is worn
out, misshapen or has lost its elasticity and fails to drop tightly into
the hollowed seat, it should be replaced with a new one. Sometimes the
ball is covered with a slimy coating which can easily be wiped off. To
replace the ball, shut off the water supply (a stop is installed underneath
the tank where the water may be conveniently shut off at this point) and
empty the tank or place a stick under the ball float lever-arm to hold
it up, thereby shutting off the intake cock and preventing the tank from
refilling. Then unscrew the ball from the lower lift wire and attach a
new ball of the same diameter as the old one. (Note: some old
tank balls swell from age and absorption of water.)
If the collar or seat of the discharge opening is
corroded or grit-covered, it should be scraped and sand-papered until
it is smooth and forms a uniform bearing for the stopper.
Straighten or replace bent lift wires so that the
ball drops squarely into the hollowed seat.
A leaky, waterlogged float ball holds the supply valve
open and does not completely shut off the water. If the rod which connects
the tank float to the supply valve has become bent, it may prevent the
float from reaching its full height, thus leaving the valve open and allowing
leakage. This rod should be straightened and a little oil applied to the
lever joints to insure smooth action.
Sometimes the tank will not fill sufficiently or will
fill to overflowing. These difficulties may be corrected without disturbing
the supply valve by bending the rod attached to the tank float upward
or downward. If the rod is bent upward, the water will rise higher in
the tank, and if downward, the water level will be lowered.
An overflow tube or pipe is provided in the closet
tank to take care of the water in case it should rise above its accustomed
level which should be at least 3/4 of an inch below the top of the overflow.
While there is not much danger of its becoming stopped up, it might be
well to examine it occasionally to see that it is in working order.
If water rises to the top of the overflow pipe an
adjustment or new fill-valve assembly is necessary. Consult your plumber
if in doubt.
Some Plumbing Codes, require the use of pressure balanced
bath/shower valves to prevent scalding in new homes and remodeling. Your
plumber can suggest the proper unit for your application.
There is more potential for the scalding of a person
showering if the pressure fluctuates. Most people aren't aware that young
children and older persons can be scalded much sooner than adults. Lowering
the water temperature at the water heater will minimize the potential
danger at the tub spout or shower head and is the best preventive action
which can be taken to prevent scalding.
A small child doesn't have to soak in overly hot tap
water to get scalded. Tragically, injury can happen literally in the blinking
of an eye. 150 degree water can scald in just 1/2 second, 140 degrees
scalds in just I second, but it takes four minutes for water at 120 degrees
POINT OF CAUTION - - Never let a child bathe
unattended, because of the danger of scalding and injury. In addition,
always turn cold crater on first, followed by the hot water until the
desired temperature is achieved. That way, no one is exposed to straight
You need not rush to buy another shower head if the
one you have suddenly gives off an uneven spray. It's probably clogged
with mineral deposits which build up in the shower head and distort the
If the shower head holes are clogged, remove the face
of the shower head, clean the back surface and free holes with a coarse
needle. The latest shower heads on the market are all self-cleaning and
need no such attention. The only positive preventive measures are investing
in a water softener or shower filter. When changing shower heads, wrap
adhesive tape around the packing nut or pad the wrench jaws with a cloth
so you won't mar the finish.
Shower curtains made of fabric such as heavy drill
or canvas can be put into the washing machine or laundry tub. All other
shower curtains should be washed by spreading flat on a table and sponging
with sudsy water. Rinse the curtain with clear water, then wipe with a
clean cloth. Turn the curtain over and repeat on the other side. Then
replace on the shower rod and spread it out straight to dry. While you're
at it, give the shower rod a good cleaning.
Clean prefabricated shower cabinets with soap and
hot water, but never with a gritty abrasive. New shower cabinets usually
have fiberglass or acrylic walls which will not withstand heavy scouring
powders. If you stand in it to wash the inside walls of the cabinet the
receptor should be protected by a heavy cloth or papers.
Chrome plating is a hard and durable finish that requires
little attention except for the occasional washing with soap and water.
Salt air or other corrosive atmospheres have a destructive
effect on chrome. Where chromium- plated fittings are exposed to these
agents, it is important to wash them frequently. After they are washed
and dried, it is advisable to apply a protective coating such as ordinary
Green spots may appear on chromium plating. If this
happens, prevent the rust from spreading by scouring the spots with the
same kind of powder which manufacturers recommend for enameled, cast iron
fixtures. When the spots have been removed, apply a Fin of wax. Your plumber
will be glad to help you select a good cleanser.
You can't get along without hot water. Therefore,
take care of the source--the water heater.
If you have a gas or electric water heater,
keep the temperature dial setting at or below the suggested Factory Energy
Savings Settings listed on the water heater. Above that mark means excessive
wear on the water heater and the potential for scalding.
The burner of a gas-fired water heater is easily accessible
and should be checked by your plumber periodically to keep it clear of
dust or sediment. The flame at full fire should be a light to dark blue.
If the flame is more orange or yellow, the gas pressure or air flow needs
to be adjusted.
You can keep your water bills low by tempering all
hot water as it is used. Letting the hot water faucet run on and on wastes
not only water but fuel as well. With all water heaters, plan your hot
water needs and you'll be delighted with the savings you get
All domestic water heaters are required to be equipped
with a relief valve as a safety feature to prevent damage from excessive
pressure and temperature. There is always danger that this valve may become
frozen or corroded from long disuse. For this reason, it is advisable
to trip the lever of this valve manually every two or three months to
be sure it will operate freely if an emergency arises. Note:
The discharge will be hot water that will need to be contained in a pan
or bucket or allowed to drain to a floor drain.
If you find a leak in your plumbing system shut off
the water supply and call your plumbing contractor at once. Water supply
systems are under high pressure. Temporary repairs are only temporary
and wrapping the pipe usually fails. Leaks must have immediate attention,
since they can progress into a serious break in a hurry.
Thawing Frozen Pipes
Frozen plumbing pipes, although inconvenient, do not
constitute a calamity. The calamity may come if the pipes are thawed with
a blow torch, and if the open flame or the torch is allowed to come too
close to combustible material, such as insulation, wooden joists or flooring.
Another danger from the use of a torch arises when
both ends of a pipe are clogged with ice and when the heat is applied
in the center. The application of the heat of the torch at the center
of the pipe is likely to cause the water to flash into steam potentially
causing an explosion with disastrous results for the user of the torch.
It is far better to adopt the slower and more conservative
procedure of melting ice by the use of a blow dryer, or heat gun.
Preventing Frozen Pipes
Before the cold freezing weather sets in, make sure
that all the garden hoses outside your home are disconnected. Failing
to do so can cause not only the hose but also the hose bib to which it
is connected, to freeze and be damaged.
This is especially important with anti-freeze hydrants.
The hose must be disconnected to make the faucet freeze-proof. Failure
to do so will trap water in the faucet body, which then can freeze. If
the hose is disconnected, the anti-freeze faucet can properly drain, and
this will prevent freezing.
Water pipes which are exposed to freezing temperatures
or drafts should be covered with insulation. Whenever possible it is best
to drain systems not being used in severely cold weather. Small water
pipes will freeze quicker than will waste or sewer pipes.
Never leave a garage door open in severely cold weather,
if there is plumbing in the garage. The cold and draft can freeze water
lines in minutes. Pipes located in unheated basements or garages should
be insulated with a commercial covering.
When pipes are laid underground they should be below
the frost line to prevent freezing.
Noises in the Plumbing System
In designing the plumbing system for a new house,
a plumbing contractor will endeavor to make it as noiseless as possible.
Manufacturers of plumbing fixings are making every effort to reduce the
noise connected with the operation of their equipment, and contractors
have been very successful in eliminating much of the noise formerly associated
with plumbing systems.
Because so much of the noise is due to water traveling
at a high velocity, it follows that whatever can be done to reduce the
velocity of the water will correspondingly reduce the noise in the system.
It is for this reason that it is so important not to skimp on the size
of the water supply piping. Larger pipe will not only provide a more adequate
supply of water but will reduce noise.
There are three general types of noises found in some
of the older plumbing systems. These are water hammer, whistling and chattering.
Water hammer is the thump in the piping heard when
faucets or valves are turned off abruptly. There is no excuse for water
hammer. It can usually be eliminated by the installation of an air chamber
or short length of pipe in the wall where each supply pipe enters a plumbing
In some cases, however, the ordinary type of air chamber
will not prevent water hammer. In such cases, special devices known as
shock arrestors should be installed on the main line near the meter or
as close as possible to the cause of the noise.
Sometimes water hammer is due not to the plumbing
in the house in which it is heard but to a condition outside of the house,
either along the water main or in a neighboring house. In such cases,
skillful detective work by an experienced master plumber is necessary
to ferret out the source of the trouble and to plan corrective methods.
Water hammer should not be permitted to go on indefinitely.
The noise is only an audible symptom of what is going on in the piping.
The piping is being subjected to the wear and tear of a multitude of shock
waves. The result will be leaks in piping, tanks or fixtures unless the
condition is corrected.
Chattering in the piping may be caused by loose pipes,
by pipes rubbing against a metal projection, by worn faucet washers or
looseness of other inside parts.
Whistling is caused by the speed of water flowing
through piping which is usually too small. A pressure reducing valve will
help as will a general straightening out of the plumbing system. Whistling
is most common at bends and tees in the pipe.
"Sweating" pipes and plumbing fixtures in summer-time
or during seasonal changes are not a sign of faulty plumbing. Due to condensation
of water vapor in the air, beads of moisture will form in warm weather
on any pipes and fixtures containing cold water.
Normally, when not in use, the water and fixtures
will worm rapidly to room temperature and the condensation will stop.
When a closet tank or other fixture continues to sweat for hours after
it has been used, it is a sign that cold water is continuing to flow through
it, possibly due to an improper adjustment of the tank valve or a leak.
Sweating pipes can be wrapped with an insulation material
which prevents the condensation and formation of moisture.
Odors in the Plumbing System
The well-designed and correctly installed plumbing
system is odorless. Odors are most likely to arise from leaks in the waste
or vent piping or from traps which have lost their water seal. In an incorrectly
installed system, there are, of course, many opportunities for odors to
result from defects in the system, particularly if it is not properly
Unusual odors should never be ignored. Such odors
are often an indication that sewer gas is present. Sewer gas, while not
always deadly, is noxious and capable of causing headaches and other minor
illnesses. Sewer gas is foul smelling air and should be prevented from
entering the house.
If it is suspected that sewer gas is entering through
a leak in the piping, a plumber will subject the system to a test either
by means of smoke, water or oil of peppermint. The test will indicate
the location of the leak.
In order to explain how the sewer gas may enter a
house through a plumbing fixture, it is necessary to clarify the function
of traps and vents. Every plumbing fixture is the terminus of the city
water supply system and the beginning of the city sewerage system. The
faucets control the water supply. The traps and vents control the sewer
air. They do so by a very simple method. Sewer air will not penetrate
a water barrier. Therefore, a device is employed which keeps several inches
of water between the house air and the sewer air. This is the trap, which
is plainly visible under such plumbing fixtures as sinks and lavatories.
It is built into water closets. In the case of bathtubs and shower cabinets,
it is usually concealed in the floor or basement.
A trap, however, would lose its water seal by siphonic
action every time a fixture is used unless the air on the sewer side is
balanced with the air on the house side. This is the function of the vents.
Occasionally, due to changes in atmospheric conditions, a compactly vented
trap will lose its seal.
Usually, however, when a trap loses its seal it is
due either to incorrect design of the vents, absence of vents or to evaporation
of the water in the trap. Traps under fixtures that are used infrequently
should be filled with water from time to time to insure an adequate trap
Draining Plumbing in a Vacant House
If your house is to be vacated during cold weather
and the heating system turned off, follow this procedure:
Shut off the water supply at the main shut-off valve
at the street. Then beginning with those on the top floor, open all faucets
and leave them open. When water stops running from these faucets, open
the cap on the main shut off valve in the basement and drain the remaining
water into a pail or tub. Remember that this cap must be closed after
the faucets have run dry or the house water supply will flow from this
valve and flood the basement.
Remove all water in the traps under sinks, water closets,
bathtubs, and lavatories by opening the clean out plugs at the bottom
of traps and draining them into a pail. If no plugs are provided, use
a force pump or other method to siphon the water out. Sponge all the water
out of the water closet bowl. Clean out all water in the flush tank.
Fill all traps with a non-freezing solution such as
mineral oil, windshield washing fluid or RV type anti-freeze.
Drain all hot water tanks. Most water tanks are equipped
with a vented tube at the top which lets air in and allows the water to
drain out the faucet at the bottom. Make sure all horizontal pipes drain
properly. Air pressure will get rid of trapped water in these pipes, but
occasionally the piping may have to be disconnected and drained. To be
safe have your plumber check your entire plumbing system.
If your house is heated by hot water or steam, drain
the heating pipes and boiler before leaving. Burners and pilots should
be completely out and the main water supply turned off at the basement
wall or street. Draw off the water from the boiler by opening the draw-off
valve at the lowest point in the system.
Open the water supply valve to the boiler so no water
will be trapped above it. If you have a hot water system, begin with the
highest radiators and open the air valve on each as fast as the water
lowers. Every radiator valve must be opened on a one inch pipe system
to release condensation.
Note: When you return home, refill all the
systems BEFORE lighting the hot water heater or boilers.
Where and How to Shut Off Water
Knowing where and how to shut off water for the entire
house or any part of it can be mighty important in an emergency. That's
why it is extremely important for all members of the family to know where
the valves are and in which direction they should be turned to shut off
One way to identify the valves is to have a tag on
each valve indicating its function, that is, which fixtures or group of
fixtures it controls. Valve- identifying tags may be obtained from plumbing
dealers. Many plumbers are glad to offer a valve tagging service to their
customers or prospective customers.
Another method of identification is by means of a
valve chart. Because this is somewhat more elaborate, it is usually employed
only for houses with several bathrooms. A drawing is made of the basement
piping with all the valves indicated. The valves are numbered on the chart
and tags with corresponding numbers are placed on the valves. Still another
idea which aids in identification is to paint pipes a distinctive color.
Obviously, the most important valve in the house is
the main shut-off valve for the entire plumbing system. This valve, generally
located on the house side of the water meter, usually has a handle like
a wheel If it has not been used in many years, it may require a wrench
to turn it. Because the easy operation of this valve in case of emergency
is so important, it is advisable to place a few drops of oil around the
valve handle once or twice a year. This will prevent the sticking action
The shut-off valve may be the ground-key type with
a small hole bored in its side for draining the pipes after the water
is shut off or it may be a drain and stop with a cap nut covering the
drain opening. In either case, close the opening before turning the water
off. Unless this is done, water will spurt with force.
Where no means has been provided for shutting off
a drain opening, drive a small wooden peg into it until the pressure is
relieved by draining the piping that is exposed.
In addition to the main strut-off valve at the meter,
the well plumbed house has individual shut-off valves on the branch lines
leading to individual fixtures, groups of fixtures or equipment such as
water heaters, water softeners, automatic washers, etc.
Many contractors, when installing plumbing fixtures,
provide separate strut-off valves or stops for each individual fixture.
These will be found on the supply lines below the fixture. These individual
stops are a great convenience to regulate water flow in case of repairs
as well as emergencies.
Understanding Backflow Prevention Programs
Some agencies, through the enforcement of the Federal
Clean Water Act, were given the task of protecting our potable water supplies.
It clarified that water purveyors must protect the public water supply
from contamination by an outside source, through implementation of a Backflow
Conformance to these state requirements minimizes
the possibility for the water using public to inadvertently contaminate
or pollute the domestic water system or the public water supply.
This program requires the installation of a backflow
prevention device in the plumbing system where the possibility of a cross
connections may take place. A cross connection. is an arrangement of piping
or faucets which allows the potable water supply to come into contact
with a contaminant.
An example of a potential cross connection is a lawn
irrigation systems, where fertilizers, chemicals or other contaminants
can come into contact with the potable water supply through the irrigation
There are several types of backflow prevention devices
used today. The type of device is determined by the degree of hazard presented
by the possible "cross connection".
Testing of Backflow Prevention Devices
In the case of a residential or commercial irrigation
system, a reduced pressure principle backflow preventer (RP device or
RPZ) is required between the potable water supply and the irrigation system.
These devices are not only required by law, but also due to the requirements
of the backflow prevention program the devices are required to be tested
annually by a certified backflow prevention tester. The annual test is
to ensure that the device is working properly and is a requirement of
the areas' cross connection control program.
Most licensed plumbing contractors have one or more
certified testers in their employ and will be happy to provide this service
Leakage from an RP Device
Leakage from a backflow preventer is normally attributed
to foreign matter lodging on the seating area of the internal check valve
seats. The majority of the time this can be corrected by simply flushing
the device which will dislodge any loose particles.
However, the spillage from the dump port does provide
a "warning signals that the device is in need of maintenance.The needed
service should be performed by a Certified Backflow Prevention Tester.
Sump Pump. If you have a sump pump, be sure
that it is always in good operating condition so that it will be ready
to function when it is needed. Oil it carefully in accordance with the
manufacturer's instructions. Make it operate occasionally by tripping
the lever after filling the basin particularly with water. Unless you
do this every three or four months, there is danger that corrosion may
cause a sticking of the shaft when operation is required.
Backwater Valve. The function of this valve
is to prevent the sewer from backing up into the house during heavy rains.
Most backwater valves operate automatically. A valve with a butterfly
action closes against the sewer on the house side.
Sometimes however, debris lodges against the seat
of the valve so that it cannot close tightly. There are also manually
operated valves, that have a wheel handle to shut them down. Sometimes,
debris (mop strings, etc.) can accumulate or collect near the valve seat,
which prevents it from closing tightly. With automatic backwater valves,
removing the lid, cleaning the seat, and greasing the hinge pin on the
valve gate annually will guarantee that the valve will operate as expected
when it is called upon to prevent the water from coming into your basement.
With the manual type of valve it is best to operate this valve manually
every six months in order that (1) all members of the family may be familiar
with the location of the valve with its function, and where the wheel
for manual operation is stored; and (2) in order that the manual operation
may keep the valve free from corrosion and lessen the chances for debris
interfering with the valves closing.
Vapors from flammable liquids can explode and catch
fire, causing death or severe burns. That is why it's vitally
important, that you should NEVER use flammable liquids such as gasoline,
adhesive solvents, lighter fluid, mineral spirits, paint thinner and kerosene,
around water heaters, furnaces, or any appliance with the potential for
flame or sparks.
Keep flammable products far away from the water heater
or furnace, stored in an approved container, tightly closed and out of
children’s' reach. Flammable products, improperly stored or used
near an open flame give off invisible vapors that can travel the length
of a house and be ignited by any of a dozen or more household sources
of flame or spark. A few precautionary measures can prevent a tragedy
from taking place.
When Calling the Plumber...
You can help your plumber by telling him, to the best
of your knowledge, exactly what's wrong when you talk to him on the telephone.
If the water closet is leaking, tell him it's the
water closet. If it's the lavatory, don't merely say that "there's a leak
in the bathroom" and expect him to tell you what to do until he gets there.
There are a thousand and one tools and parts in his
plumbing store, and he can't be expected to carry them all. So, when you
ask for his help, give him as much information as you can. When he arrives,
tell him everything that has been done to the defective part of the plumbing.
It will speed his work and lower your plumbing bill.